Imagine you're in Glendale, AZ, on a very hot summer day. The sun is shining bright, and you're looking forward to relaxing in your cool home. But suddenly, your air conditioner starts blowing hot air instead of cool. This is what happened to a homeowner with over heated compressor repair of 2.5 ton split unit in Glendale AZ.
Service Call Description:
The homeowner's complaint was pretty straightforward - their air conditioner was blowing hot air, making their home feel like an oven. When the technician from America's Home Services arrived at the scene, he quickly identified the root of the problem. The air conditioner's compressor was overheated and in thermal protection mode.
What's more, this particular unit had no pressure switches to prevent the compressor from running at dangerously high head pressures or low pressures. This was causing severe damage to the compressor, and to make matters worse, the unit was running low on Freon, which is crucial for keeping it oiled and maintaining high head pressure. There was also a suspicion of combustibles mixed in with the Freon.
Furthermore, the technician discovered a restriction in the system and a potential Freon leak, possibly at the indoor evaporator coil. To add to the woes, the indoor coils were rusted out, and the compressor had sustained significant damage. It was clear that a mere repair wouldn't suffice; the unit needed to be replaced.
The technician recommended replacing the old, damaged air conditioning unit with a brand-new one. The client was presented with two options:
- Cash or Check Discount Price: $10,000
- Credit Card Financing Price: $10,450 with low payments of $137.94 at a fixed 9.99% interest rate, and no prepayment penalties. Wells Fargo financing was available for those who chose this option.
The cost of the service also included the trip fee of $250. The new unit recommended was a 2.5 Ton Split Unit First Company Air Handler, suitable for a two-story building. Due to its location on the 2-story roof, a large crane with a boom was required to install the condenser.
Execution and Results:
Upon the client's agreement, the technician swiftly procured and installed the new air conditioning unit. The installation involved careful handling of the heavy condenser unit and precise connection of all components. The technician ensured that the system was running efficiently and cooling the home effectively.
Client Communication and Advice:
The technician communicated the situation to the client clearly and concisely. They explained the issues with the old unit, the necessity of replacement, and the available options for the new unit and financing. The client was fully informed and confident in their decision to proceed with the replacement.
In Glendale, where summer temperatures can be unforgiving, having a reliable air conditioner is not a luxury but a necessity. America's Home Services came to the rescue of a homeowner facing a malfunctioning air conditioner. By promptly diagnosing the problem, offering suitable replacement options, and executing the installation flawlessly, they restored comfort to the client's home.
Stay Cool with Your AC Experts in Glendale
If you're in Glendale and find yourself in a similar hot predicament with your air conditioner, don't hesitate to choose America's Home Services for all your HVAC needs. With their commitment to customer satisfaction and expertise in handling AC issues, they are your go-to solution for keeping cool in the scorching Glendale heat. Stay comfortable; choose America's Home Services for your HVAC needs.